Have a Safe Day!
Monday, October 3, 2011
Orange Tape on 3-Pronged Electrical Tools and Extension Cords
Good afternoon to all I.D.I. employees: All Safety Coordinators should have been provided with a roll of orange tape from your Superindendents. We began a new quarter on 10/1/11 for our Assured Grounding Program. You are to inspect, test and color-code with orange tape all 3 pronged electrical tools and extension cords. All electrical tools and cords need to be visually inspected. If you see any defects in the cords such as bare wires, severe kinks, missing or damaged ground prong, the cord pulling away from the plug end housing, etc., then that tool or cord would need to be immediately removed from service and reported to your Foreman. If your tool/cord passes the visual inspection, your next step is to test the cord with a receptacle tester. First, you should test the oulet that you will be plugging your cord into to ensure that it is properly wired. You should see 2 yellow lights lit up on your tester and the red light should be off. This means the outlet is working appropriately. Next, plug your cord into the outlet and then test the cord with the receptacle tester. Again, you should see the same light pattern as mentioned above and this would mean the cord passed the test and it is good and safe to use. Any other light pattern means that there is a problem with the cord and the cord needs to be removed from service and reported to your Foreman. If the cord passes the visual inspection and the cord tester test, you should then remove the previous quarter's green electrical tape and install the red electrical tape about 1" down from both plug ends. Your cord is now in compliance with our 3rd quarter's Assured Ground Program. The orange tape shall remain in place from 10/1/11 through 12/30/11. You are not quite done yet! You now need to visually inspect all electrical cords and tools on a daily basis and if any defects are found, the cord needs to be immediately removed from service. Thank you for taking the time to ensure your electrical tools and cords are in safe working order. Your actions may prevent one of our family members from sustaining an electrical shock type injury or worse yet and electrocution. If you have any questions regarding our Assured Grounding Program, please call our Safety Director, Peter Graham, at (847) 417-1689.